Nuotraukos yra skirtos tik informaciniams tikslams. Peržiūrėkite produkto specifikaciją
Nira EB lentynos
|The Nilar energy storage system solutions can be configured according to different setups, creating flexibility and a user-friendly experience for the customers. The energy storage system can be scaled up in order to meet your energy demand. Each energy storage system can be extended to include four units, where one unit acts as the Master and up to three units as Servants.
To enable the Nilar energy storage system to operate according to the specifications, an inverter is required to handle charging and discharging of the energy storage and for the conversion between AC/DC. An Energy Management System (EMS) is also required in order to control when and where the power should be delivered. Depending on the chosen energy storage set-up, the EMS manages various system functions such as power management and inverter management. The EMS can either communicate with the Nilar BMS or directly with the inverter to initiate charging or discharging of the battery bank.
DOWNLOAD THE CATALOGUE
Battery size is determined by a number of application-specific features such as load profile (kW), desired system voltage (V) and required runtime (h). Another important aspect of your energy storage solution is the inverter. Different applications require different size of the inverter. Nilar can assist you upon request to find the correct inverter to match your energy storage system.
|Rack||Art. no.||Description||No. of battery packs||Pack voltage [V]||System voltage [V]||Rated capacity [Ah]||Energy [kWh]||Weight [kg]||Depth [mm]||Height [mm]||Width [mm]|
|ECI-600V-48kWh-M||20-0024||Rack 48 kWh Master||40||120||600||80||48||1402||615||1996||1509|
|ECI-600V-48kWh-S||20-0026||Rack 48 kWh Servant||40||120||600||80||48||1402||615||1996||1509|
|ECI-576V-57,6kWh-M||20-0025||Rack 57,6 kWh Master||40||144||576||100||57,6||1610||615||1996||1509|
|ECI-576V-57,6kWh-S||20-0027||Rack 57,6 kWh Servant||40||144||576||100||57,6||1610||615||1996||1509|